- About The Store
- Home Safety FAQs
View Cart 0
To be notified when this item is back In Stock, please enter your Email Address below:
You Save: $34.81 (29% Off)
The First Alert Hearing Impaired LED Strobe Light features a powerful LED strobe light that's proven to be extremely efficient in providing assistance for individuals with hearing impairments. The intuitive use of a Smart Strobe light carries the ability to distinguish between Smoke/Heat and CO dangers. First Alert Smart Strobe Lights include a wide compatibility range and can be interconnected with First Alert and BRK Smoke, CO, Smoke/CO Combination and Heat alarms (up to 18 detectors, 12 can be smoke alarms).
First Alert's Hearing Impaired LED Strobe Light features a 10 Year Limited Warranty. This hearing impaired strobe light meets UL Standards and fulfills the requirements of the Americans with Disabilities Act.
This LED strobe light is for you if:
Where to place LED strobe lights:
First Alert Strobe Light SLED177
* California and New York Residents - Please note this alarm is not compliant with your State's 10 Year Sealed Battery Alarm Legislation Requirements.
In this guide, we'll be showing you how to install First Alert Hardwired Smoke and Carbon Monoxide Alarms. Here are a few items you'll need before starting the installation process: Needle-nose pliers or utility knife, screwdriver, wire stripper, wire nuts and a ladder.
Hardwired Smoke or Carbon Monoxide Alarm Requirements:
To begin, turn off power at the junction box and connect your alarm to the building's electrical wiring.
|Attach to black wire on power connector|
|Attach to white wire on power connector|
Standalone (single-station) alarm: This wire is not needed; tuck the orange wire into the junction box.
If you are installing more smoke or carbon monoxide alarms, you'll want to repeat the process throughout the building. Interconnected smoke and co alarms must meet all requirements:
The same fuse or circuit breaker must power all interconnected alarms.
Up to 18 compatible detectors can interconnect, with a limit of 12 smoke alarms.
The total length of wire interconnecting the alarms should be less than 1,000 ft. (300 meters). This type of wire is commonly available at hardware and electrical supply stores.
All wiring must conform to all local electrical codes and NFPA 70 (NEC). Refer to NFPA 72, NFPA 101, and your local building code for more information.
Interconnect wiring diagram:
If you have any doubts or reservations about these interconnect requirements, please contact an experienced electrician to install your wiring and hardwired alarms.
Once you've installed your hardwired alarms, you'll want to restore power to the junction box. Under regular operation, the power indicator light on the alarm will shine/blink to indicate that it is receiving AC power.
Here's how you can test standalone or interconnected alarms:
Standalone Alarms: Press and hold the Test/Silence button until the unit triggers an alarm.
Interconnected Alarms: Press and hold the Test/Silence button until the first unit triggers an alarm. All interconnected detectors should sound off. Repeat this process to test each alarm in the interconnected series.
We make it as easy as possible to ensure you get the lowest prices available:
Average score based on 3 reviews