Wireless Interconnect Hardwired Smoke Alarm
The First Alert SA521CN-3ST Interconnected Smoke Alarm allows owners to create an interconnected fire alarm system without the cost and hassle of wiring. Use this smoke detector to replace an existing hardwired smoke alarm and then install additional First Alert Wireless alarms for an interconnected safety network (additional alarms sold separately). This hardwired smoke detector can connect and communicate with up to 18 compatible alarms, so when one alarm is triggered, the entire system reacts. An integrated battery backup ensures the smoke alarm continues to work even during power outages.
Photoelectric Sensor Warns of Smoldering Fires
The First Alert Wireless Interconnect Smoke Alarm comes equipped with a photoelectric sensor to provide the earliest possible warning of fire. The sensor is optimized to detect larger smoke particles produced by smoldering fires, such as those caused by unextinguished cigarettes. It also distinguishes between real threats and smoke/vapor produced during showering, cooking, and other everyday activities, helping minimize the number of false alarms. A patented smoke entry system helps ensures reliable detection by providing a direct air pathway to the sensor.
Interconnectivity for Larger Areas
The hardwired smoke alarm can be connected to other compatible BRK and First Alert hardwired alarms for larger buildings such as dormitories, office buildings, and apartments. Connect up to 18 compatible devices: up to 12 smoke alarms and six compatible devices like horns and repeaters. The communication distance (range) between any two First Alert Wireless Interconnect Alarms is typically 50 ft. (15 meters) inside of a home. Some features of a home, such as the number of floors, number/size of rooms, furniture and types of building materials used may reduce the range of wireless interconnect alarms. First Alert helps you create a comprehensive warning system for you and your property.
Battery Backup for Continuous Coverage
In the event of a power outage, the smoke alarm is still able to function thanks to its two AA backup batteries. An indicator sound is emitted when the batteries need to be replaced. The inclusion of an optional drawer and mounting bracket lock will discourage tampering.
Test and Silence Button
Mute Button has been included to serve the dual purpose of silencing nuisance alarms and testing the functionality of your alarm.
EZ-Access Battery Door
The addition of an EZ Access Battery Door removes the hassles and burdens associated with changing your alarm's batteries.
First Alert Wireless Interconnect Hardwired Smoke Alarm SA521CN-3ST
- Wireless inter-connectivity, wirelessly connect up to 18 interconnect alarms in your home and when one sounds, they all sound for increased whole-home protection.
- 120v ac hardwired, easily replace one existing hardwired alarm with First Alert SA521 alarm and then add Wireless Interconnect battery operated alarms to connect wireless alarms with hardwired alarms--when one sounds, they all sound.
- Battery backup provides consistent protection for added safety during power outages.
- Photoelectric smoke sensing provides optimal protection from smoldering fires, while reducing false alarms like those caused by cooking fires and shower steam.
- Mute button silences unnecessary alarms immediately. It also tests alarm function with same button.
- Eco-friendly, completely recyclable as an electronic device.
- EZ access battery door, no need to remove alarm from ceiling to change battery.
- Optional theft-prevention lock, when activated, batteries and/or alarm cannot be removed without proper tools.
- 2AA batteries included.
- Loud 85db alarm.
- Smoke alarms should be replaced every 10 years for maximum protection.
- Meets UL217 standard.
- FCC compliant.
- 10 Year Limited Warranty.
- Product Dimensions (LxWxH): 5 x 2 x 5 in.
- Product Weight: 1 lb.
How to Install First Alert SA521CN-3ST Hardwired Smoke Alarms:
In this guide, we'll be showing you how to install First Alert Hardwired Smoke and Carbon Monoxide Alarms. Here are a few items you'll need before starting the installation process: Needle-nose pliers or utility knife, screwdriver, wire stripper, wire nuts and a ladder.
Hardwired Smoke or Carbon Monoxide Alarm Requirements:
- 120V household electrical circuit (unswitched 120VAC)
- Standard wiring junction box to a 4 in. (10 cm) size, on either the ceiling or wall
- Selecting an appropriate location to install your smoke and carbon monoxide alarms (see below guidelines for additional information):
- When installing an alarm on the wall, the top edge of an alarm should be placed between 4 in. (100 mm) and 12 in. (300 mm) from the wall/ceiling line.
- When installing an alarm on the ceiling, place the alarm as close to the center as possible.
- In either case, install the alarm at least 4 in. (100 mm) from where the wall and ceiling meet.
- First Alert Smoke Alarm FAQs
- First Alert Carbon Monoxide Alarm FAQs
Connecting First Alert Hardwired Alarms to 120V Wiring
To begin, turn off power at the junction box and connect your alarm to the building's electrical wiring.
- Locate the junction box and turn off power
- Remove the power connector from the new alarm's packaging
- Using wire nuts, attach the hot (black), neutral (white), and interconnect (orange) wires
|Attach to black wire on power connector
|Attach to white wire on power connector
Standalone (single-station) alarm: This wire is not needed; tuck the orange wire into the junction box.
- Strip 1/2 in. from the orange wire on the connector
- Use a wire nut to attach it to the orange wire in the junction box (see image below).
Mounting First Alert Hardwired Alarms
- Secure the mounting bracket to the ceiling or wall using screws (included in the package)
- Insert the power connector into the plug on the back of your alarm
- Tuck any hanging wires into the junction box
- Position the base of the alarm onto the bracket and turn it clockwise until it's secured
- Remove the pull-tab to activate the backup battery
Installing Additional and/or Interconnecting First Alert Hardwired Alarms
If you are installing more smoke or carbon monoxide alarms, you'll want to repeat the process throughout the building. Interconnected smoke and co alarms must meet all requirements:
The same fuse or circuit breaker must power all interconnected alarms.
Up to 18 compatible detectors can interconnect, with a limit of 12 smoke alarms.
The total length of wire interconnecting the alarms should be less than 1,000 ft. (300 meters). This type of wire is commonly available at hardware and electrical supply stores.
All wiring must conform to all local electrical codes and NFPA 70 (NEC). Refer to NFPA 72, NFPA 101, and your local building code for more information.
Interconnect wiring diagram:
If you have any doubts or reservations about these interconnect requirements, please contact an experienced electrician to install your wiring and hardwired alarms.
Restoring Power and Testing Hardwired Alarms
Once you've installed your hardwired alarms, you'll want to restore power to the junction box. Under regular operation, the power indicator light on the alarm will shine/blink to indicate that it is receiving AC power.
Here's how you can test standalone or interconnected alarms:
Standalone Alarms: Press and hold the Test/Silence button until the unit triggers an alarm.
Interconnected Alarms: Press and hold the Test/Silence button until the first unit triggers an alarm. All interconnected detectors should sound off. Repeat this process to test each alarm in the interconnected series.
Q: What is a mesh network and how do the First Alert Wireless Interconnect smoke detectors intercommunicate?
A: First Alert Wireless Interconnect smoke alarms operate on a "mesh network" to integrate smoke alarms for better safety and response in an emergency. All of the First Alert Wireless Interconnect alarms send, receive and resend the initiating alarm's signal. Why is this important? Let's say the signal is blocked from reaching the master bedroom alarm either by distance or some obstruction in the home. With First Alert Wireless Interconnect, the mesh network of alarms re-routes and re-sends the signal via the other alarms, providing a greater chance all alarms will receive the signal. The "mesh network" is a more reliable means of wireless communication.
Q: What is the proper placement of smoke alarms?
A: It is important that you have the proper placement for your smoke alarms. Install your alarms at least 20 feet from appliances like furnaces and ovens, which produce combustion particles. Alarms should be at least 10 feet from high humidity areas like showers and laundry rooms, and at least 3 feet from heat/AC vents. Be sure to install a smoke alarm in each bedroom, one at the top of each stairwell, and one on every level.
Q: My smoke alarm keeps chirping and beeping. Why does my smoke alarm chirp intermittently?
It is likely that the reason your smoke alarm keeps chirping and beeping is that the battery is low. Whenever your smoke alarm keeps chirping, replace the battery immediately.
Other reasons include: It could be a different device or appliance such as a security system, monitor, carbon monoxide alarm, or other device which has a similar low battery or alert signal. Some of the same factors that cause unwanted alarms can cause intermittent alarms: dust and insects in the alarm or power interruptions in hardwired alarms. Improper wiring on AC or AC/DC smoke alarms. AC alarms will chirp every 5 seconds if the interconnect wire is grounded. The orange interconnect wire should NEVER be grounded; it should only be used to interconnect other smoke alarms or compatible devices.
Q: Why doesn't my smoke alarm sound when I push the test button?
It is important that you frequently test your smoke alarms. When you are testing your smoke alarm, there are a number of reasons why the alarm might not sound:
- You may not be holding the test button down long enough. Try holding it down for up to 10 seconds (20 seconds on photoelectric models) .
- Your battery may not be installed properly or snapped all the way in place. Even if the alarm sounded briefly when the battery touched the terminals, you still need to make sure it is snapped securely in place. If the battery is loose, in cannot power the smoke alarm properly. After installing new batteries, be sure to test your smoke detector.
- Your AC power may not be on. AC and AC/DC units will have a power indicator light (red or green) that shines continuously when they are receiving electrical power.
- If you have a 10-Year model, the smoke alarm may not have been properly activated. If the tab broke away before the alarm was activated, you can use a toothpick to move the switch over to test the alarm.
Q: Why does my smoke alarm go off when I install a battery or turn on the AC power?
It is normal for smoke alarms to go off and sound briefly (up to 5-10 seconds) when you install a new battery or when they are powered up. If the alarm continues to go off and no smoke is present, the cause may be one of the following:
- There may be insufficient battery power, try new batteries.
- Problems with voltage or insufficient electrical power (brown out) may cause a continuous weak sounding alarm. For AC or AC/DC models, temporarily disconnect power at the service panel until the brown out is over. If you do not restore the AC power, your smoke alarms cannot warn you of a fire.
- Incompatible warning device. If an incompatible alarm or auxiliary device is linked into a series of AC or AC/DC smoke alarms it may cause the system inadvertently go off.
Q: My smoke alarm keeps chirping, even with a new battery. What is causing this?
There are a number of possible causes for your smoke alarm to keep chirping even with a new battery.
- It is possible that your smoke alarm "silence" button was pushed by mistake. The alarm will now "chirp" once a minute for up to 15 minutes before resetting.
- Are you sure it's the smoke alarm? Funny to ask, but other devices have similar low battery chirps or warning tones.
- Your "new" batteries may not be fresh. If batteries are stored, especially in cold areas like refrigerators, they lose their charge more quickly. Always check the freshness date on the package when buying new batteries. Keep plenty of replacement batteries on hand so that you are sure to always be protected by your smoke alarms.
Q: I lost my First Alert smoke alarm owner's manual. How can I get a new one?
First Alert smoke alarm owner's manuals are available online for download at no cost. Find your alarm in our Smoke Alarms
Q: Why does the National Fire Protection Association (NFPA) recommend that home smoke alarms be replaced after 10 years?
Smoke alarms have a limited life. Although each smoke alarm and all of its parts have passed many stringent tests and are designed to be as reliable as possible, any of these parts could fail over time. Therefore, you must test the devices weekly. The unit should be replaced immediately if it is not operating properly. The performance of smoke alarms older than 10 years is simply not reliable. To ensure your family's safety, all carbon monoxide and smoke/CO combination alarms need to be replaced every 5-7 years. All smoke alarms need to be replaced every 10 years.
If it's time to replace your alarms, consider the NEW 10-Year Life series and never have to worry about a battery replacement for the life of the alarm.10-Year alarms are available in smoke
First Alert SA521CN-3ST Wireless Interconnect Hardwired Smoke Alarm (1039830) Videos
If you are interested in ordering a large quantity of items you may qualify for volume pricing discounts. Volume Discount Pricing is a great way for customers to save big on large, bulk orders of most items available in our store. Please send a bulk order request
to our friendly sales staff so they may create a quote and provide personal service for your order! You will receive a response within 1-2 business days and our office hours are Monday through Friday, 8am-5pm CST.
We make it as easy as possible to ensure you get the lowest prices available:
Send A Request Now
- Let us know what products & the quantities you are interested in.
- Get a detailed quote from a dedicated sales rep.
- Our warehouse ships directly to you.
- You enjoy the savings & are now a preferred customer.
Direct From Warehouse Pricing